Types of Power Plants Electric Power Plants Coal|Fired Power Plants Southern Company Power Plants Power Plant Operator Jobs Solar Power Nuclear Power Plants by State
| Powerplant | PowerPlant | Powertrain | Aircraft_powerplant | Reciprocating_engine | Engine | Power_Plant_(Gamma_Ray_album) | Central_Islip_State_Hospital_Powerplant | Powerplant_(Album) | Salt_River_Hydroelectric_Powerplant | Enloe_Dam_and_Powerplant | Airframe_and_Powerplant | Hydroelectric_powerplant | Biogas_powerplant | WCW_Powerplant | Nuclear_powerplant | Shelbyville_Nuclear_Powerplant | List_of_naval_ship_classes_in_service | Hybrid_electric_powerplant | Georgetown_Steam_Plant | Blenheim-Gilboa_Powerplant | Krafla_Power-Plant | Reykjanes_Power-Plant | Chipilima_Hydro_Powerplant | Nesjavellir_Power-Plant | Jaguar_V12_engine | Combined_gas_and_steam | Navajo_Generating_Station | Moyes_Dragonfly | Mitsubishi_8A8_engine | Naharayim | Aircraft_engine_controls | Oroville-Thermalito_Complex | Mitsubishi_3G8_engine | Smuggler-Union_Hydroelectric_Power_Plant | Saturn_I4_engine | Niagara_Falls_hydroelectric_generating_plants | Jetex_engine | Litostroj | Mark_Winger | BMW_P60B40 | Grand_Coulee_Dam | Shiraz_Biogas_Power_Plant | Heinkel_He_111 | Shoshone_Project | Keswick_Dam | MacApp | Motorboat |
|This article needs additional citations for verification. (February 2011)|
A power station (also referred to as a generating station, power plant, powerhouse or generating plant) is an industrial facility for the generation of electric power. At the center of nearly all power stations is a generator, a rotating machine that converts mechanical power into electrical power by creating relative motion between a magnetic field and a conductor. The energy source harnessed to turn the generator varies widely. It depends chiefly on which fuels are easily available, cheap enough and on the types of technology that the power company has access to. Most power stations in the world burn fossil fuels such as coal, oil, and natural gas to generate electricity, and some use nuclear power, but there is an increasing use of cleaner renewable sources such as solar, wind, wave and hydroelectric.
The world's first power station was designed and built by Lord Armstrong at Cragside, England in 1868. Water from one of the lakes was used to power Siemens dynamo's. The electricity supplied power to lights, heating, produced hot water, ran an elevator as well as labour-saving devices and farm buildings.
The first public power station was the Edison Electric Light Station, built in London at 57, Holborn Viaduct, which started operation in January 1882. This was an initiative of Thomas Edison that was organized and managed by his partner, Edward Johnson. A Babcock and Wilcox boiler powered a 125 horsepower steam engine that drove a 27 ton generator called Jumbo, after the celebrated elephant. This supplied electricity to premises in the area that could be reached through the culverts of the viaduct without digging up the road, which was the monopoly of the gas companies. The customers included the City Temple and the Old Bailey. Another important customer was the Telegraph Office of the General Post Office, but this could not be reached though the culverts. Johnson arranged for the supply cable to be run overhead, via Holborn Tavern and Newgate.
In September 1882 in New York, the Pearl Street Station was established by Edison to provide electric lighting in the lower Manhattan Island area. The station ran until destroyed by fire in 1890. The station used reciprocating steam engines to turn direct-current generators. Because of the DC distribution, the service area was small, limited by voltage drop in the feeders. The War of Currents eventually resolved in favor of AC distribution and utilization, although some DC systems persisted to the end of the 20th century. DC systems with a service radius of a mile (kilometer) or so were necessarily smaller, less efficient of fuel consumption, and more labor-intensive to operate than much larger central AC generating stations.
AC systems used a wide range of frequencies depending on the type of load; lighting load using higher frequencies, and traction systems and heavy motor load systems preferring lower frequencies. The economics of central station generation improved greatly when unified light and power systems, operating at a common frequency, were developed. The same generating plant that fed large industrial loads during the day, could feed commuter railway systems during rush hour and then serve lighting load in the evening, thus improving the system load factor and reducing the cost of electrical energy overall. Many exceptions existed, generating stations were dedicated to power or light by the choice of frequency, and rotating frequency changers and rotating converters were particularly common to feed electric railway systems from the general lighting and power network.
Throughout the first few decades of the 20th century central stations became larger, using higher steam pressures to provide greater efficiency, and relying on interconnections of multiple generating stations to improve reliability and cost. High-voltage AC transmission allowed hydroelectric power to be conveniently moved from distant waterfalls to city markets. The advent of the steam turbine in central station service, around 1906, allowed great expansion of generating capacity. Generators were no longer limited by the power transmission of belts or the relatively slow speed of reciprocating engines, and could grow to enormous sizes. For example, Sebastian Ziani de Ferranti planned what would have been the largest reciprocating steam engine ever built for a proposed new central station, but scrapped the plans when turbines became available in the necessary size. Building power systems out of central stations required combinations of engineering skill and financial acumen in equal measure. Pioneers of central station generation include George Westinghouse and Samuel Insull in the United States, Ferranti and Charles Hesterman Merz in UK, and many others.
Thermal power stations
In thermal power stations, mechanical power is produced by a heat engine that transforms thermal energy, often from combustion of a fuel, into rotational energy. Most thermal power stations produce steam, and these are sometimes called steam power stations. Not all thermal energy can be transformed into mechanical power, according to the second law of thermodynamics. Therefore, there is always heat lost to the environment. If this loss is employed as useful heat, for industrial processes or district heating, the power plant is referred to as a cogeneration power plant or CHP (combined heat-and-power) plant. In countries where district heating is common, there are dedicated heat plants called heat-only boiler stations. An important class of power stations in the Middle East uses by-product heat for the desalination of water.
The efficiency of a steam turbine is limited by the maximum steam conditions produced and is not directly a function of the fuel used. For the same steam conditions, coal, nuclear and gas power plants all have the same theoretical efficiency. Overall, if a system is on constantly (base load) it will be more efficient than one that is used intermittently (peak load). Steam turbines generally operate at higher efficiency when operated a full capacity.
Besides use of reject heat for process or district heating, one way to improve overall efficiency of a power plant is to combine two different thermodynamic cycles. Most commonly, exhaust gases from a gas turbine are used to generate steam for a boiler and steam turbine. The combination of a "top" cycle and a "bottom" cycle produces higher overall efficiency than either cycle can attain alone.
Power plants that can be dispatched (scheduled) to provide energy to a system include:
Non-dispatchable plants include such sources as wind and solar energy; while their long-term contribution to system energy supply is predictable, on a short-term (daily or hourly) base their energy must be used as available since generation cannot be deferred. Contractual arrangements ( "take or pay") with independent power producers or system interconnections to other networks may be effectively non-dispatchable.
All thermal power plants produce waste heat energy as a byproduct of the useful electrical energy produced. The amount of waste heat energy equals or exceeds the amount of energy converted into useful electricity . Gas-fired power plants can achieve 50% conversion efficiency while coal and oil plants achieve around 30–49%. The waste heat produces a temperature rise in the atmosphere which is small compared to that produced by greenhouse-gas emissions from the same power plant. Natural draft wet cooling towers at many nuclear power plants and large fossil fuel-fired power plants use large hyperboloid chimney-like structures (as seen in the image at the right) that release the waste heat to the ambient atmosphere by the evaporation of water.
However, the mechanical induced-draft or forced-draft wet cooling towers in many large thermal power plants, nuclear power plants, fossil-fired power plants, petroleum refineries, petrochemical plants, geothermal, biomass and waste-to-energy plants use fans to provide air movement upward through downcoming water, and are not hyperboloid chimney-like structures. The induced or forced-draft cooling towers are typically rectangular, box-like structures filled with a material that enhances the mixing of the upflowing air and the downflowing water.
In areas with restricted water use, a dry cooling tower or directly air-cooled radiators may be necessary, since the cost or environmental consequences of obtaining make-up water for evaporative cooling would be prohibitive. These coolers have lower efficiency and higher energy consumption to drive fans, compared to a typical wet, evaporative cooling tower.
Where economically and environmentally possible, electric companies prefer to use cooling water from the ocean, a lake, or a river, or a cooling pond, instead of a cooling tower. This type of cooling can save the cost of a cooling tower and may have lower energy costs for pumping cooling water through the plant's heat exchangers. However, the waste heat can cause the temperature of the water to rise detectably. Power plants using natural bodies of water for cooling must be designed to prevent intake of organisms into the cooling machinery. A further environmental impact is that aquatic organisms which adapt to the warmer discharge water may be injured if the plant shuts down in cold weather.
Water consumption by power stations is a developing issue.
In recent years, recycled wastewater, or grey water, has been used in cooling towers. The Calpine Riverside and the Calpine Fox power stations in Wisconsin as well as the Calpine Mankato power station in Minnesota are among these facilities.
Power stations can also generate electrical energy from renewable energy sources.
Dams built to produce hydroelectricity impound a reservoir of water and release it through one or more water turbines, connected to generators, and generate electricity, from the energy provided by difference in water level upstream and downstream.
A pumped-storage hydroelectric power plant is a net consumer of energy but can be used to smooth peaks and troughs in overall electricity demand. Pumped storage plants typically use "spare" electricity during off peak periods to pump water from a lower reservoir or dam to an upper reservoir. Because the electricity is consumed "off peak" it is typically cheaper than power at peak times. This is because the "base load" power stations, which are typically coal fired, cannot be switched on and off quickly so remain in service even when demand is low. During hours of peak demand, when the electricity price is high, the water pumped to the high reservoir is allowed to flow back to the lower reservoir through a water turbine connected to an electricity generator. Unlike coal power stations, which can take more than 12 hours to start up from cold, the hydroelectric plant can be brought into service in a few minutes, ideal to meet a peak load demand. Two substantial pumped storage schemes are in South Africa, one to the East of Cape Town (Palmiet) and one in the Drakensberg, Natal
A solar photovoltaic power plant converts sunlight into direct current electricity using the photoelectric effect. Inverters change the direct current into alternating current for connection to the electrical grid. This type of plant does not use rotating machines for energy conversion.
Solar thermal power plants are another type of solar power plant. They use either parabolic troughs or heliostats to direct sunlight onto a pipe containing a heat transfer fluid, such as oil. The heated oil is then used to boil water into steam, which turns a turbine that drives an electrical generator. The central tower type of solar thermal power plant uses hundreds or thousands of mirrors, depending on size, to direct sunlight onto a receiver on top of a tower. Again, the heat is used to produce steam to turn turbines that drive electrical generators.
Wind turbines can be used to generate electricity in areas with strong, steady winds, sometimes offshore. Many different designs have been used in the past, but almost all modern turbines being produced today use a three-bladed, upwind design. Grid-connected wind turbines now being built are much larger than the units installed during the 1970s, and so produce power more cheaply and reliably than earlier models. With larger turbines (on the order of one megawatt), the blades move more slowly than older, smaller, units, which makes them less visually distracting and safer for airborne animals.
Marine energy or marine power (also sometimes referred to as ocean energy or ocean power) refers to the energy carried by ocean waves, tides, salinity, and ocean temperature differences. The movement of water in the world’s oceans creates a vast store of kinetic energy, or energy in motion. This energy can be harnessed to generate electricity to power homes, transport and industries.
The term marine energy encompasses both wave power — power from surface waves, and tidal power — obtained from the kinetic energy of large bodies of moving water. Offshore wind power is not a form of marine energy, as wind power is derived from the wind, even if the wind turbines are placed over water.
The oceans have a tremendous amount of energy and are close to many if not most concentrated populations. Ocean energy has the potential of providing a substantial amount of new renewable energy around the world.
Salinity gradient energy is called pressure-retarded osmosis. In this method, seawater is pumped into a pressure chamber that is at a pressure lower than the difference between the pressures of saline water and fresh water. Freshwater is also pumped into the pressure chamber through a membrane, which increase both the volume and pressure of the chamber. As the pressure differences are compensated, a turbine is spun creating energy. This method is being specifically studied by the Norwegian utility Statkraft, which has calculated that up to 25 TWh/yr would be available from this process in Norway. Statkraft has built the world's first prototype osmotic power plant on the Oslo fiord which was opened on November 24, 2009.
The power generated by a power station is measured in multiples of the watt, typically megawatts (106 watts) or gigawatts (109 watts). Power stations vary greatly in capacity depending on the type of power plant and on historical, geographical and economic factors. The following examples offer a sense of the scale.
Many of the largest operational onshore wind farms are located in the USA. As of 2011, the Roscoe Wind Farm is the second largest onshore wind farm in the world, producing 781.5 MW of power, followed by the Horse Hollow Wind Energy Center (735.5 MW). As of July 2013, the London Array in United Kingdom is the largest offshore wind farm in the world at 630 MW, followed by Thanet Offshore Wind Project in United Kingdom at 300 MW.
As of April 2012, the largest photovoltaic (PV) power plants in the world are led by India's Gujarat Solar Park rated at 605 megawatts. A planned installation in China will produce 2000 megawatts at peak.
Solar thermal power stations in the U.S. have the following output:
Large coal-fired, nuclear, and hydroelectric power stations can generate hundreds of Megawatts to multiple Gigawatts. Some examples:
Gas turbine power plants can generate tens to hundreds of megawatts. Some examples:
The rated capacity of a power station is nearly the maximum electrical power that that power station can produce. Some power plants are run at almost exactly their rated capacity all the time, as a non-load-following base load power plant, except at times of scheduled or unscheduled maintenance.
However, many power plants usually produce much less power than their rated capacity.
In some cases a power plant produces much less power than its rated capacity because it uses an intermittent energy source. Operators try to pull maximum available power from such power plants, because their marginal cost is practically zero, but the available power varies widely—in particular, it may be zero during heavy storms at night.
In some cases operators deliberately produce less power for economic reasons. The cost of fuel to run a load following power plant may be relatively high, and the cost of fuel to run a peaking power plant is even higher—they have relatively high marginal costs. Operators keep power plants turned off ("operational reserve") or running at minimum fuel consumption ("spinning reserve") most of the time. Operators feed more fuel into load following power plants only when the demand rises above what lower-cost plants (i.e., intermittent and base load plants) can produce, and then feed more fuel into peaking power plants only when the demand rises faster than the load following power plants can follow.
The power station operator has several duties in the electricity-generating facility. Operators are responsible for the safety of the work crews that frequently do repairs on the mechanical and electrical equipment. They maintain the equipment with periodic inspections and log temperatures, pressures and other important information at regular intervals. Operators are responsible for starting and stopping, the generators depending on need. They are able to synchronize and adjust the voltage output of the added generation with the running electrical system, without upsetting the system. They must know the electrical and mechanical systems in order to troubleshoot solve/fix problems in the facility and add to the reliability of the facility. Operators must be able to respond to an emergency and know the procedures in place to deal with it.
|Wikimedia Commons has media related to Power plants.|